On the use of continuous-wavelet transform for fault location in distribution power systems. PERETTO, L., Tinarelli, R., Corsi, S., PAOLONE, M., Nucci, C., A., BORGHETTI, A., A., B., Corsi, S., C., N., PAOLONE, M., PERETTO, L., & Tinarelli, R. *International journal of electrical power and energy systems*, 28(9):608-617, s.n, 2006.

Paper Website abstract bibtex

Paper Website abstract bibtex

The paper illustrates a procedure based on the continuous-wavelet transform (CWT) for the analysis of voltage transients due to line faults, and discusses its application to fault location in power distribution systems. The analysis carried out shows that correlation exists between typical frequencies of the CWT-transformed signals and specific paths in the network covered by the traveling waves originated by the fault. The paper presents a procedure for determining fault location in MV distribution systems, which exploits the above-mentioned correlation. The MV distribution system analysed in the paper is accurately represented by means of an EMTP model; various fault types and network characteristics are examined. The paper presents also the basic concepts of a measurement and fault location prototype system with distributed architecture.

@article{ title = {On the use of continuous-wavelet transform for fault location in distribution power systems}, type = {article}, year = {2006}, identifiers = {[object Object]}, keywords = {Fault location}, pages = {608-617}, volume = {28}, websites = {http://www.sciencedirect.com/science/article/pii/S0142061506000792}, publisher = {s.n}, city = {s.l}, id = {7ce79e73-2707-38c3-8b2e-c46ef9a42216}, created = {2019-05-10T12:11:11.309Z}, file_attached = {true}, profile_id = {f7c25345-a8b5-3d31-977d-34baa516d876}, group_id = {7dcc2f99-6e61-3683-a6e6-764f3bce95b4}, last_modified = {2019-05-10T12:11:15.948Z}, read = {true}, starred = {false}, authored = {false}, confirmed = {true}, hidden = {false}, citation_key = {Borghetti2006608}, source_type = {article}, notes = {<b>From Duplicate 1 (<i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b>From Duplicate 2 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]<br/><br/><b>From Duplicate 2 (<i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Peretto, L; Tinarelli, R; Corsi, S; PAOLONE, M; Nucci, C A; Borghetti, A; A., BORGHETTI)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Borghetti, A; Corsi, S; Nucci, C A; Paolone, M; Peretto, L; Tinarelli, R )<br/></b><br/>Selection of Papers from 15th Power Systems ComputationConference, 2005 PSCC’0515th Power Systems Computation Conference<br/><br/><b>From Duplicate 2 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b><br/>From Duplicate 3 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]}, private_publication = {false}, abstract = {The paper illustrates a procedure based on the continuous-wavelet transform (CWT) for the analysis of voltage transients due to line faults, and discusses its application to fault location in power distribution systems. The analysis carried out shows that correlation exists between typical frequencies of the CWT-transformed signals and specific paths in the network covered by the traveling waves originated by the fault. The paper presents a procedure for determining fault location in MV distribution systems, which exploits the above-mentioned correlation. The MV distribution system analysed in the paper is accurately represented by means of an EMTP model; various fault types and network characteristics are examined. The paper presents also the basic concepts of a measurement and fault location prototype system with distributed architecture.}, bibtype = {article}, author = {PERETTO, L and Tinarelli, R and Corsi, S and PAOLONE, M and Nucci, C A and BORGHETTI, A and A., BORGHETTI and Corsi, S and C., NUCCI and PAOLONE, M and PERETTO, L and Tinarelli, R}, journal = {International journal of electrical power and energy systems}, number = {9} }

Downloads: 0

{"_id":"Czbf8mznpcRg6cbNv","bibbaseid":"peretto-tinarelli-corsi-paolone-nucci-borghetti-a-corsi-etal-ontheuseofcontinuouswavelettransformforfaultlocationindistributionpowersystems-2006","authorIDs":[],"author_short":["PERETTO, L.","Tinarelli, R.","Corsi, S.","PAOLONE, M.","Nucci, C., A.","BORGHETTI, A.","A., B.","Corsi, S.","C., N.","PAOLONE, M.","PERETTO, L.","Tinarelli, R."],"bibdata":{"title":"On the use of continuous-wavelet transform for fault location in distribution power systems","type":"article","year":"2006","identifiers":"[object Object]","keywords":"Fault location","pages":"608-617","volume":"28","websites":"http://www.sciencedirect.com/science/article/pii/S0142061506000792","publisher":"s.n","city":"s.l","id":"7ce79e73-2707-38c3-8b2e-c46ef9a42216","created":"2019-05-10T12:11:11.309Z","file_attached":"true","profile_id":"f7c25345-a8b5-3d31-977d-34baa516d876","group_id":"7dcc2f99-6e61-3683-a6e6-764f3bce95b4","last_modified":"2019-05-10T12:11:15.948Z","read":"true","starred":false,"authored":false,"confirmed":"true","hidden":false,"citation_key":"Borghetti2006608","source_type":"article","notes":"<b>From Duplicate 1 (<i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b>From Duplicate 2 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]<br/><br/><b>From Duplicate 2 (<i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Peretto, L; Tinarelli, R; Corsi, S; PAOLONE, M; Nucci, C A; Borghetti, A; A., BORGHETTI)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Borghetti, A; Corsi, S; Nucci, C A; Paolone, M; Peretto, L; Tinarelli, R )<br/></b><br/>Selection of Papers from 15th Power Systems ComputationConference, 2005 PSCC’0515th Power Systems Computation Conference<br/><br/><b>From Duplicate 2 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b><br/>From Duplicate 3 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]","private_publication":false,"abstract":"The paper illustrates a procedure based on the continuous-wavelet transform (CWT) for the analysis of voltage transients due to line faults, and discusses its application to fault location in power distribution systems. The analysis carried out shows that correlation exists between typical frequencies of the CWT-transformed signals and specific paths in the network covered by the traveling waves originated by the fault. The paper presents a procedure for determining fault location in MV distribution systems, which exploits the above-mentioned correlation. The MV distribution system analysed in the paper is accurately represented by means of an EMTP model; various fault types and network characteristics are examined. The paper presents also the basic concepts of a measurement and fault location prototype system with distributed architecture.","bibtype":"article","author":"PERETTO, L and Tinarelli, R and Corsi, S and PAOLONE, M and Nucci, C A and BORGHETTI, A and A., BORGHETTI and Corsi, S and C., NUCCI and PAOLONE, M and PERETTO, L and Tinarelli, R","journal":"International journal of electrical power and energy systems","number":"9","bibtex":"@article{\n title = {On the use of continuous-wavelet transform for fault location in distribution power systems},\n type = {article},\n year = {2006},\n identifiers = {[object Object]},\n keywords = {Fault location},\n pages = {608-617},\n volume = {28},\n websites = {http://www.sciencedirect.com/science/article/pii/S0142061506000792},\n publisher = {s.n},\n city = {s.l},\n id = {7ce79e73-2707-38c3-8b2e-c46ef9a42216},\n created = {2019-05-10T12:11:11.309Z},\n file_attached = {true},\n profile_id = {f7c25345-a8b5-3d31-977d-34baa516d876},\n group_id = {7dcc2f99-6e61-3683-a6e6-764f3bce95b4},\n last_modified = {2019-05-10T12:11:15.948Z},\n read = {true},\n starred = {false},\n authored = {false},\n confirmed = {true},\n hidden = {false},\n citation_key = {Borghetti2006608},\n source_type = {article},\n notes = {<b>From Duplicate 1 (<i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b>From Duplicate 2 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - BORGHETTI, A; CORSI, S; C., NUCCI; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]<br/><br/><b>From Duplicate 2 (<i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Peretto, L; Tinarelli, R; Corsi, S; PAOLONE, M; Nucci, C A; Borghetti, A; A., BORGHETTI)<br/></b><br/><b>From Duplicate 1 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - Borghetti, A; Corsi, S; Nucci, C A; Paolone, M; Peretto, L; Tinarelli, R )<br/></b><br/>Selection of Papers from 15th Power Systems ComputationConference, 2005 PSCC’0515th Power Systems Computation Conference<br/><br/><b>From Duplicate 2 ( <i>On the use of continuous-wavelet transform for fault location in distribution power systems</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[ARTICOLO]<br/><br/><b><br/>From Duplicate 3 ( <i>On the Use of Continuous-Wavelet Transform for Fault Location in Distribution Power Networks</i> - A., BORGHETTI; CORSI, S; NUCCI, C A; PAOLONE, M; PERETTO, L; TINARELLI, R )<br/></b><br/>[RELAZIONE]},\n private_publication = {false},\n abstract = {The paper illustrates a procedure based on the continuous-wavelet transform (CWT) for the analysis of voltage transients due to line faults, and discusses its application to fault location in power distribution systems. The analysis carried out shows that correlation exists between typical frequencies of the CWT-transformed signals and specific paths in the network covered by the traveling waves originated by the fault. The paper presents a procedure for determining fault location in MV distribution systems, which exploits the above-mentioned correlation. The MV distribution system analysed in the paper is accurately represented by means of an EMTP model; various fault types and network characteristics are examined. The paper presents also the basic concepts of a measurement and fault location prototype system with distributed architecture.},\n bibtype = {article},\n author = {PERETTO, L and Tinarelli, R and Corsi, S and PAOLONE, M and Nucci, C A and BORGHETTI, A and A., BORGHETTI and Corsi, S and C., NUCCI and PAOLONE, M and PERETTO, L and Tinarelli, R},\n journal = {International journal of electrical power and energy systems},\n number = {9}\n}","author_short":["PERETTO, L.","Tinarelli, R.","Corsi, S.","PAOLONE, M.","Nucci, C., A.","BORGHETTI, A.","A., B.","Corsi, S.","C., N.","PAOLONE, M.","PERETTO, L.","Tinarelli, R."],"urls":{"Paper":"https://bibbase.org/service/mendeley/f7c25345-a8b5-3d31-977d-34baa516d876/file/287e5e4c-d18a-fab1-3038-1375d22831b3/Peretto_et_al___2006___On_the_use_of_continuous_wavelet_transform_for_fault_location_in_distribution_power_systems.pdf.pdf","Website":"http://www.sciencedirect.com/science/article/pii/S0142061506000792"},"bibbaseid":"peretto-tinarelli-corsi-paolone-nucci-borghetti-a-corsi-etal-ontheuseofcontinuouswavelettransformforfaultlocationindistributionpowersystems-2006","role":"author","keyword":["Fault location"],"downloads":0},"bibtype":"article","creationDate":"2019-05-10T12:14:08.378Z","downloads":0,"keywords":["fault location"],"search_terms":["use","continuous","wavelet","transform","fault","location","distribution","power","systems","peretto","tinarelli","corsi","paolone","nucci","borghetti","a.","corsi","c.","paolone","peretto","tinarelli"],"title":"On the use of continuous-wavelet transform for fault location in distribution power systems","year":2006}